I'm using an Analog output (VTS Datatype) writing to a PLC DINT by way of a "Numeric Input" on the page to allow user to enter a passcode (EQU in PLC) to permit the action of a selector switch, right below the numeric input box.
When you enter the correct number, "it is retained in the VTS tag browser" and will work okay. But I need a way to clear it out after a minu
Hello friends, I have a serious problem. VTS does not open on the server. I have two servers, one is a backup of the other, VTS only starts if the network cables are disconnected, clicking on RUN locks in 50% in the final step "Starting tags". Does anyone know how to solve?
I am working with a Siemens S7 TIA Portal program and I am trying to pull the part type from the PLC into the VTSCADA system. The issue I am having with the String I\O is I am only getting the DEC form of the tag and not the CHARACTER values. In the PLC in a watch table when I look at the exact tag in DEC I get the value of 2565 but in CHAR I get DB 10 (FW part type). is there something I can do
I am working with an Omron Cj2H. Programmed analog inputs and reading into a DM. Positive values are performing okay, but as soon as I go slightly negative ( reverse flow), then the number jumps to 65535. This is telling me it is wrapping around. I have tried using negative values in the scaling, but have not been successful at this point. I can watch the channel in the plc and it remains nega
I am building a plant from scratch. The plant has different types of equipment and all I can see in VTScada are various pumps, valves, and motors. Has anyone built or have access to bar screens, conveyor belts, weir gates, or anything else that might be useful?
I'll be bringing up a replacement server for one that got a hit by lightening and I need to know the trick for getting VTscada to only poll the serial modbus connections from the active server in a redundant server config.
Hello, I am evaluating VTScada for our facility and am working with the scadalight. I have not worked with Omron Plcs in many years and need some information. My plc has some levels which are stored in a data area (ie D0700). The PLC resides on our network (ie 192.168.10.20). From the program, I do know they set the port to 2120 instead of the default 9600. I am not sure which settings to use
Hello, I'm using VTScada Light for a POC (proof of concept) in my customer. The application works well for a fell minutes, but after this it lose the communication and doens't update the registers values. Is there anything to do to solve this problem?