Tank cut-away images are designed to work with the Color Fill widget. Place a cut-away on a tank and then set the color of that cut-away to something that will be unique on the page. Orange is a great choice. Now, place a Color Fill widget on top of the cut-away and set its Changed Color to match the color of the cut-away. The Color Fill will be visible only where it overlaps the matching co
Answer - Alarm notes can be found on the Alarm Page in the right-most column, it will contain an icon if the alarm contains a note. Simply click the icon to view the note. You will also see the note on the Operator Notes page. More on notes: www.trihedral.com/operator-notes
Answer - A small portion of application settings require the app to be restarted when they are changed, though most do not. Compiling some types of custom code will require an app restart as well, though this does not apply to pages, graphics and tag types.
Answer - There are several ways to export data from the VTScada Historical Database.
From the Historical Data Viewer (HDV) you can export the visible values using the Export Wizard Button at the top of the HDV. See help: www.trihedral.com/help/Content/OP_HDV/OP_HDVExport.htm?Highlight=Export%20historical.
You can use the standard reports page to easily export data for specific tags and timef
Answer - Typically, all modifications to drivers are made directly by Trihedral personnel to ensure compatibility with future software releases. In exceptional circumstance, you should contact us directly.
Our SupportPlus team regularly answers this question:
Q: I just updated to a newer version of VTScada and now my modems no longer work!
A: Customers using the modem dialer feature of the Alarm Notification System must ensure that they apply Windows updates on a regular basis. Updates to VTScada will often include modem drivers that have been patched to work with the latest Microsoft updat
Does VTScadaLIGHT support the Anywhere Internet Client?
The mobile client seems to work fine in a browser, but when I log into the AIC throw a web browser all I see is a white page. A logon failed notification gets logged to the System Event DB even though I know I'm using the correct credentials.
Afternoon All; I am trying to poll a Modbus flow meter. The register I am polling is a floating point, and at this time just looking to get a proper HEX response. Below is a couple of request and response. The request is correct as I have tested with a Mdbus master modbus simulator. It is looking to me that there is a inter-character time out issue. But any thoughts, questions or solutions wou